Ignition 7.6.6 (b2014040112) | 64-bit
Allen-Bradley Drivers 1.6.6 (b2014040112)
Windows Server 2008 R2 SP1
We had a PLC ( ControlLogix 1756-L61/B ) worked on and when the programmer put the PLC back into remote run the gateway still saw the device in program mode.
We switched the PLC from REM to RUN and still the gateway refused. We restarted the fiber connection and nothing.
Clicking restart on the Allen Bradley Driver module from the gateway configuration pages is what fixed it, even though the other AB PLCs (a mix of Control, Compact, and Micro Logix) were all shown correctly in Remote Run.
Any ideas? I don’t like the idea of restarting the AB module being a fix since now this makes me the first guy to call when a problem occurs.