I’m having an issue reading tag values from a CompactLogix using v20 firmware. I can connect to the PLC fine and read all the tag structures. The diagnostics show a connection. Everything looks good, except I cannot read any values form any of the tags.
When I try to read a value from the OPC Quick Client I get the following:
Quality: [Bad_CommunicationError] A low level communication error occurred.
What’s the exact firmware version of the device? Although the device drivers short-hand to v21 as the cutoff, some AB devices past a certain v20 revision aren’t fully compatible with our legacy drivers. Try the newer Allen Bradley Logix driver and see if it connects successfully.